Static Voltage Stability Margin Enhancement Using SVC and TCSC
Reactive power limit of power system is one of the major causes of voltage instability. The only way to save the system from voltage instability is to reduce the reactive power load or add additional reactive power to reaching the point of voltage collapse. In recent times, the application of FACTS devices is a very effective solution to prevent voltage instability due to their fast and very flexible control. In this paper, voltage stability assessment with SVC and TCSC devices is investigated and compared in the modified IEEE 30-bus test system. The fast voltage stability indicator (FVSI) is used to identify weakest bus and to assess the voltage stability of power system.
Digital Object Identifier (DOI): doi.org/10.5281/zenodo.1336454Procedia APA BibTeX Chicago EndNote Harvard JSON MLA RIS XML ISO 690 PDF Downloads 3515
 A. Guzmán, D. Tziouvaras, E. O. Schweitzer and Ken E. Martin, "Local and wide-area network protection systems improve power system reliability,” Schweitzer Engineering Laboratories technical papers, 2004.
 A. Wiszniewski, "New criteria of voltage stability margin for the purpose of load shedding,” IEEE trans. Power del, vol. 22, no. 3, July 2007, pp. 1367-1371.
 IEEE "Proposed terms and definitions for flexible AC transmission system (FACTS)”, IEEE Transactions on Power Delivery, Vol. 12, No. 4, pp. 1848-1853, October 1997.
 A. Hernandez, M.A. Rodriguez, E. Torres, P. Eguia, "A Review and Comparison of FACTS Optimal Placement for Solving Transmission System Issues”, Renewable Energy and Power Quality Journal (RE&PQJ), No.11, March 2013.
 M. Amroune, A. Bourzami, and T. Bouktir, "Improvement of Transient Stability Margin in Power Systems with Integrated Wind Generation Using the SVC”, 13th International conference on Sciences and Techniques of Automatic control & computer engineering, December 17-19, 2012, Monastir, Tunisia.
 D. Thukaram and A. Lomi, "Selection of Static VAR Compensator Location and Size for System Voltage Stability Improvements”, Electrical Power System Research, vol. 54, pp. 139-150, 2000.
 Kundur P, Power System Stability and Control, EPRI Power System Engineering Series, McGraw-Hill, 1994.
 MINAMI, Shoichi, MORII, Satoshi and KAWAMOTO, Shunji "Voltage Stability Analysis for Bulk Power System by P-V and Q-V Curves Considering Dynamic Loads”, International Conference on Electrical Engineering, 2008.
 B. Gao, G. K. Morison and P. Kundur, "Voltage Stability Evaluation Using Modal Analysis”, IEEE Trans on Power Sys, vol. 7, pp 1529-1542, November 1992.
 Arthit Sode-Yome, Nadarajah Mithulananthan, Kwang Y. Lee, "A Maximum Loading Margin Method for Static Voltage Stability in Power Systems,” IEEE Transactions on Power Systems, vol. 21, NO. 2, May 2006.
 T. Nagao, K. Tanaka and K. Takenaka, "Development of static and simulation programs for voltage stability studies of bulk power system,” IEEE Transactions on Power Systems, vol. 12, pp: 273-281, Jan. 1997.
 K. Lba, H. Suzuki, M. Egawa, et al. "Calculation of critical loading condition with nose curve using homotopy continuation method,” IEEE Trans on Power Systems, vol. 6, pp: 584-593, May. 1991.
 Liu Zhuo. "The impedance analyses of heavy load node in voltage stability studies,” Proceedings of the CSEE, vol. 20, pp: 35-39, Apr. 2000.
 I. Musirin, T.K.A Rahman, "Novel Fast Voltage Stability Index (FVSI) for Voltage Stability Analysis in Power Transmission System,” Student Conference on Research and Development Proceedings, Shah Alam, Malaysia, July 2002.
 Mahmoud Moghavvenni, M.Faruque,”Estimation of Voltage Collapse From Local measurement of Line Power Flow and Bus Voltages”, Proc. of International conference on Electrical Power Engineering, Budapest, pp77, February 1999.
 R. Grünbaum, M. Noroozian, and B. Thorvaldsson, "FACTS: solutions to power flow control & stability problems,” ABB Review, vol. 5, 1999.
 T. J. E Miller, Reactive Power Control in Electric Systems, Wiley Interscience, 1982, vol. 4, pp. 204-214.
 H. A. Perez, E. Ache, and C. R. F. Esquivel, "Advanced SVC Models for the Newton Raphson load flow and Newton optimal power flow studies”, IEEE Transactions on the power systems, vol. 15, no. 1, pp. 129-136, February 2000.
 C. A. Caizares, "Power flow and transient stability models of FACTS controllers for voltage and angle stability studies,” Proc. 2000 IEEE Power Engineering Society Winter Meeting, pp. 8, Jan. 2000.
 Arthit Sode-Yome, Nadarajah Mithulananthan and Kwang Y. Lee, "A Comprehensive comparison of FACTS Devices for Enhancing Static Voltage Stability,” IEEE Power Engineering Society General Meeting, June 2007.
 C. A. Canlzares, Z. T. Faur, "Analysis SVC and TCSC Controllers in Voltage Collapse,” IEEE Transactions on the power systems, vol. 14, No. 1, February 1999, pp. 158-165.
 N. Talebi, M. Ehsan, S.M.T Bathaee, "Effects of SVC and TCSC Control Strategies on Static Voltage Collapse Phenomena,” IEEE Proceedings, Southeast Con, pp. 161 - 168, Mar 2004.
 N. Hingorani and L. Gyugyi, Understanding FACTS Concepts and Technology of Flexible AC Transmission Systems, Piscataway, NJ: IEEE Press/Wiley, 2000.
 Abouzar Samimi, Peyman Naderi, "A New Method for Optimal Placement of TCSC Based on Sensitivity Analysis for Congestion Management”, Smart Grid and Renewable Energy, 2012, 3, 10-16.
 C. Schaffner and G. Andersson, "Performance of a TCSC for Congestion Relief,” Proceedings of the Conference on Power Technology, St. Petersburg, 23-27 June, 2005, pp. 1-3.
 S. Meikandasivam, Rajesh Kumar Nema, and Shailendra Kumar Jain, "Selection of TCSC Parameters: Capacitor and Inductor”, International Conference on Power Electronics (IICPE), 28-30 Jan. 2011 India, pp.1-5.
 E. De Tuglie, S. M. Iannone, F. Torelli "A coherency based method to increase dynamic security in power systems”, Electric Power Systems Research. 78 (2008) 1425 – 1436.