Evaluation of the Performance of ACTIFLO® Clarifier in the Treatment of Mining Wastewaters: Case Study of Costerfield Mining Operations, Victoria, Australia
A pre-treatment stage prior to reverse osmosis (RO) is very important to ensure the long-term performance of the RO membranes in any wastewater treatment using RO. This study aims to evaluate the application of the Actiflo® clarifier as part of a pre-treatment unit in mining operations. It involves performing analytical testing on RO feed water before and after installation of Actiflo® unit. Water samples prior to RO plant stage were obtained on different dates from Costerfield mining operations in Victoria, Australia. Tests were conducted in an independent laboratory to determine the concentration of various compounds in RO feed water before and after installation of Actiflo® unit during the entire evaluated period from December 2015 to June 2018. Water quality analysis shows that the quality of RO feed water has remarkably improved since installation of Actiflo® clarifier. Suspended solids (SS) and turbidity removal efficiencies has been improved by 91 and 85 percent respectively in pre-treatment system since the installation of Actiflo®. The Actiflo® clarifier proved to be a valuable part of pre-treatment system prior to RO. It has the potential to conveniently condition the mining wastewater prior to RO unit, and reduce the risk of RO physical failure and irreversible fouling. Consequently, reliable and durable operation of RO unit with minimum requirement for RO membrane replacement is expected with Actiflo® in use.
Digital Object Identifier (DOI): doi.org/10.5281/zenodo.1474895Procedia APA BibTeX Chicago EndNote Harvard JSON MLA RIS XML ISO 690 PDF Downloads 1059
 Seyed Mohsen Samaei, Shirley Gato-Trinidad, Ali Altaee, The application of pressure-driven ceramic membrane technology for the treatment of industrial wastewaters – A review, Separation and Purification Technology, Volume 200, 2018, Pages 198-220, ISSN 1383-5866.
 Recycled Water, Case Study: Bendigo Mining Water Treatment Plant,VIC(7ML/day),
 Mak water, Case Studies, < https://www.makwater.com.au/case-studies/> Access Date: (27/08/2018).
 Citor Desalinators, Mine Site Archives,
 Tara Tyrell, Queensland Mining &Energy Bulletin, Veolia to deliver Reverse Osmosis plant for Kirkland lake Gold in Victoria ,Australia, < https://www.qmeb.com.au/veolia-to-deliver-reverse-osmosis-plant-for-kirkland-lake-gold-in-victoria-australia/> Access Date: (27/08/2018).
 APT Aqua Pure Water Filters & Water Treatment Systems, Water Treatment Products-Mining Sites,
 Water desalination +reuse , Veolia Water Tech to deliver RO reuse plant for gold mine,
 B. Chakravorty, A. Layson, Ideal feed pretreatment for reverse osmosis by continuous microfiltration, Desalination, 110 (1997) 143-149.
 Veolia Water Solutions & Technologies, Operation and Maintenance Manual Mandalay WTP, in, 2014.
 Gregory Chris, Mandalay Resources-Costerfield, < https://www.mandalayresources.com/properties/costerfield/> Access Date: (27/08/2018).
 SRK Consulting (Australasia) Pty Ltd, Costerfiled Operation, Victoria, Australia NI 43-101 Technical Report, 2017.
 Environment Protection Authority Victoria- Australia, Mandalay Resources Costerfield Operations Pty Ltd License No:109992, 2014.
 S. Hajbabania, Mandalay Water Treatment Plant, Veolia Water Solutions & Technologies.
 Water Treatment Guide, RO membranes, < http://www.watertreatmentguide.com/membrane_condition.htm> Access Date: (27/08/2018).
 Environment Protection Authority Victoria- Australia, Mandalay Resources Costerfield Operations Pty Ltd Annual Performance Statement, Statement Period: 01 July 2016 to 30 June 2017.
 Kezia Kezia, Damien, Voysey, J. Dwyer, Veolia - Victorian Mine RO plant: Autopsy Report for RO Membranes, Wastewater Futures Pty Ltd, 2016.
 Veolia Water Technologies Clarification for Drinking Water Treatment: ACTIFLO®,
 Veolia Water Technologies, ACTIFLO® Process For Wet Weather and Wastewater Treatment,
 ALS Environmental Certificate of Analysis, Environmental Division Melbourne 2015-2018.
 Environment Protection Authority Victoria- Australia, Mandalay Resources Costerfield Operations Pty Ltd Annual Performance Statement, Statement Period: 01 July 2015 to 30 June 2016.